TABLE OF CONTENTS
- Connection Instructions
- Omnimeter I v.3 Diagram
- Omnimeter II UL v.3 Diagram
- Omnimeter Pulse v.4 Diagram
- Omnimeter Pulse UL v.4 Diagram
2-wire systems can occasionally be 240 volts (Hot to Hot). Metering of these systems can be done with any of our Omnimeter models
The images and diagrams shown here are in no way exhaustive. These are just a few examples of how you might set up a metering system, and are simply intend to show what is possible. These are the options that you might consider for your metering setup:
- Do I want to read the meter(s) locally with computer or do I want a cloud based solution (EKM Push).
- What diameter and amperage rating will I need for the Current Transformers? You will need one CT for your 2-wire single phase electrical system.
- Do I need to go wireless?
- Do I have a need to daisy chain multiple Omnimeters together? This allows you to connect multiple Omnimeters in series, which can then be connected to a single communication device.
The answers to these questions should help you narrow down your options and allow you to select the products that you will need for your particular application.
For a 240 volt 2-wire system (2 Hots, no neutral) you will only need to use 1 CT. When you measure the voltage between these 2 wires you will get 240 volts.
- Turn off power to the sub-panel.
- Connect the L1 line voltage reference wire to port 7 on the Omnimeter
- Connect the L2 line voltage reference wire to port 10 on the Omnimeter.
- Connect the CT so that L1 passes through it and the arrow on the CT points towards the load.
- Connect the CT black wire to port 1 on the Omnimeter and the CT white wire to port 2 on the Omnimeter.
This video tutorial provides an example of how to install an Omnimeter Pulse v.4 on a 120/240v electrical system. You can use this video to infer how a single phase, two wire installation might go. The only absolute difference is that there will only be one CT and one voltage reference wire:
Below are diagrams showing each Omnimeter model wired to a single-phase 2-wire no-neutral electrical system, while also being RS-485 hardwired to a Push3 gateway (A to A, B to B).
Omnimeter I v.3:
Omnimeter II UL v.3:
Omnimeter Pulse v.4:
Omnimeter Pulse UL v.4:
See this model for reference of how to properly connect an Omnimeter to a 2-wire system:
Here is a link to a movable 3D model of the above diagram that you can use to see details of any side: 2-wire Single Phase EKM Omnimeter 3D Model